FRP water tank
||SMC FRP (GRP) sectional water tank
|thickness of panel:
||4mm 6mm 8mm 10mm 12mm 14mm 16mm 18mm 20mm 22mm
|Material of panel:
||polyester resin system specified in BS EN13121-1-2003
|glass fiber reinforcement is tpye "E" glass specified in ISO 2078
||SMC (sheet moulding compound) ISO 8605-2001
|Bolts and nuts:
||GBT5783-2000 , ISO4017-1999
||bracing system, vent, jointing sealant, manhole, ladder, inlet and outlet, overflow, U steel base, etc.
As manufacturer of FRP (GRP) water tank, we can supply SMC FRP sectional water tank world widely. We have been in this line for more than 20 years, we have enough experience to produce and assemble various of water tank for you.
SMC GRP sectional water tank is sheet molding compound glass fiber reinforced plastic sectional water tank. It is also called FRP water tank (fiberglass reinforced plastic water tank). It is suitable for drinking water, living water, fire water and Industrial water storage facilities, etc.
Advantages of SMC GRP water tank: light weight, no corrosion, no leakage, good water quality, wide application range, long service life, good thermal insulation performance, beautiful appearance, convenient installation, convenient cleaning and maintenance, and strong adaptability, etc.
GRP SMC sectional water tank is assembled by SMC tank panel, sealing materials, metal structure and pipe system. The size of SMC water tank panel as follows:
the thinckness of the panel as follows:
4mm, 6mm, 8mm, 10mm, 12mm, 14mm, 16mm, 18mm, 20mm, etc.
The water tank can be assembled with the size 0.125m³~3,000m³, depend on your requirement.
The GRP panels are made from high temperature press molding of compound material.
The specification of SMC molding single panel:
Tensile strength: more than 59Pa
Bending strength: more than 78Pa
Flexural strength and elastic modulus: 5900MPa
Barcol hardness: more than 30
Water absorption: less than 1.0%
The reinforcement system in water tank, lacing bar and support are stainless steel or galvanized steel.
The image show you the reinforcement sysytem inside the water tank.
The lacing bar and roof support make the water tank more stronger.
more details information, reinforcement system outside the water tank. And the inlet and outlet flanges are bolted on the side of the water tank panel.
GRP SMC water tank installation instruction:
1.The concrete foundation should be same level and the height should more than 500mm for checking.
2.Put the channel base on the concrete foundation, and ensure that the channel base is horizontal.
3.Assemble the bottom panel, ensure the connection method between panel and panel as follows: bolt--gasket--panel--rubber strip--another panel--gasket-nut, then tightening the bolt.
4.Assemble the side panel, ensure the connection method as same as the above-metioned. If reinforcement is required, the side panels need to be added auxiliary angle iron.
5.When we assemble the panel which has 45º slant bolt holes, we must loose three nuts of two side panels, then tighten 45º slant bolts, and then tighten the two side of loosing bolts.
6.Assemble the plugging, push out the plugging and add sealing gasket, angle iron, gasket and nut, then tighten the nut, glass glue.
7.Assemble the lacing bar, ensure that the lacing bar is not too tight or too loose.
8.Assemble the top cover panel.
9.Assemble the flange, ensure sealing well.
10.Assemble the ladder, ensure it is nearby the manhole.
Contact us for more details about the FRP water tank.